PYRO-SAFE CT ML
PYRO SAFE CT "system floor penetration seal" system variant for existing cable/electrical conduit penetrations and for new installations.
Fire rating EI 30 - EI 120 in accordance with EN 13501-2
Easy installation makes this system an economical fire protection barrier for existing cable/electrical conduit penetrations and for new installations in the system floor area.
Fire resistance class
EI 30 - EI 120 in accordance with EN 13501-2
Approved by Deutsches Institut für Bautechnik, Berlin.
Depending on design, services such as electrical cables and lines (excluding so-called waveguide cables) and fibre-optic cables Ø ≤ 50 mm, cable bundles Ø ≤ 100 mm (single cable Ø ≤ 21 mm) and cable conduits of PE-HD Ø ≤ 32 mm with and without cables (individual cables Ø ≤ 21 mm). The PYRO-SAFE CT ML can be filled to capacity.
Resistant to fire and flue gases; forms a layer of expanded graphite based insulating foam in the event of fire.
Cables and lines can be subsequently installed at any time without difficulty using basic tools.
Particular points to note
Must only be fitted and used in accordance with the installation instructions.
Notes on installation
Installation in rated walls, below fire doors and lightweight partition walls also possible.
The floor tiles of the system floor do not have to be rated (no requirement for the system floor's fire resistance duration).
They must only be non-flammable.
The PYRO-SAFE CT ML can be installed on one side (single-side seal with 40 mm thick melamine resin foam plugs and sealing with PYRO-SAFE FLAMMOTECT-A).