PYRO-SAFE Bag Sealing system
Variable sealing system made of fire protection bags for electric cables and power lines of all types. Fire resistance class S 90 acc. to DIN 4102-9.
Variable sealing system for cable penetration through massive walls, plasterboard walls (≥ 10 cm) and floors (≥ 15 cm).
Fire protection features
Up to 1½ hours integrity and insulation according to DIN 4102-9.
Approved by Deutsches Institut für Bautechnik, Berlin (DIBt).
National technical approval No.: Z-19.15-819 - PYRO-SAFE Bag
Fire resistant and smoke tight, space-enclosing, simple handling, can be reused multiple times.
For all types and diameters of cables (except waveguides), fibre optics, cable bundles and cable trays.
Particular points to note
Installation and handling only permitted in accordance with the approval, the installation instruction/technical drawings.
The subsequent installation of cables is (according to the approval) easy to handle and possible with a basic tool kit at any time.
Preliminary building work
Before installation in floors, fasten steel wire mesh to the bottom of the floor as a safeguard from falling out. Installation permitted even in plasterboard walls (dimensions as shown in the table on the right). Before installation in plasterboard walls, seal the reveals according to approval. For wall thicknesses < 16 cm arrange supports on the lower reveal according to the approval. If necessary, attach a removal guard (e.g. wire netting).